Monday, November 8, 2010
Peach Bottom: Cask Leakage Rate Greater than Specification
Facility: PEACH BOTTOM Event Date: 10/22/2010 SPENT FUEL STORAGE RELATED DEFECT - CASK LEAKAGE RATE GREATER THAN TECHNICAL SPECIFICATION "On 10/22/10, at 1058 EDT, a troubleshooting of Independent Spent Fuel Storage Installation (ISFSI) Cask TN-50-A indicated that a leak existed in the cask lid sealing area at a rate greater than allowed by ISFSI Cask Technical Specification (TS) Section 3.1.3, Cask Helium Leak Rate. TS 3.1.3 limits the Cask Helium Leak Rate to 1.0 E-05 ref-cc/sec. The cask is currently in unloading operations and is located within the Peach Bottom Atomic Power Station Unit 3 containment building. Preliminary review indicates that a leak exists at the weld plug that provides sealing of the drilled interseal passageway associated with the drain port penetration of the cask lid. This leak effectively provides a bypass of the main lid outer confinement seal. "This report if being submitted pursuant to 10CFR72.75(c)(1) as a result of a material defect in a weld in the cask main lid. This report is also being submitted pursuant to 10CFR72.75 ® (2) as a result of a resolution in the effectiveness of the cask confinement system. "The Certificate of Compliance for this cask is 1027 (Amendment 1). "The NRC Resident Inspector has been informed of this notification."
Subscribe to: Post Comments (Atom)
Post a Comment